Rittal CMC-III Units: Temperatures In/Out
|Distribution:||official part of Check_MK|
This check monitors the temperatures measured by
Rittal CMC-III Liquid Cooling Package Fanpacks.
These units have 6 temperature sensors, 3 for inflowing air,
3 for outflowing air.
This check handles each of those sensors individually while
cmciii_lcp_airin and cmciii_lcp_airout handle the temperature
averages of inflowing and outflowing air respectively.
Limits are configured in the Rittal device itself but can be
overridden. The state given by the Rittal device is
taken as the state of the check as follows:
If the Rittal device returns OK, the check is OK. Otherwise
the check is CRIT.
The unit name and the name of the temperature sensor
One service is created for each temperature sensor on all cmciii lcp fanpack units.