Check manual page of siemens_plc_duration
|Siemens PLC: Duration Values|
|Distribution||official part of Check_MK|
You need to use and configure the special agent
agent_siemens_plc which is using the SNAP7
library to communicate with the Siemens PLC. When you are using OMD, everything is already
installed and configured. In manual setups, you will need to ensure that the snap7 library
and python module
snap7 are installed. To make temperature values available for the check, you need to configure the memory addresses and data types to read from the device as temperature values.
The checks does not
CRIT unless you configure the thresholds for the check, as the
device does not report any thresholds. When the duration value is smaller than the previous
one, the check goes to
CRIT for one check.
Name of the device and the mode seperated by a space
One service is created for each configured duration value.